AnonymousJuly 6, 2008 at 6:20 pmPost count: 4
I’m trying to set up a scene using EZServe as the controller. All of the Insteon devices are up and responding and the timers fire and work properly. However, I am unable to get these devices to respond when creating a scene.
A couple of questions.
1) I’m using a mixture of Icon and smartlabs devices. So far I have only been able to ad an Icon device to the scene. Is this a problem and how critical is the device definition on the device set-up?
2) Is it possible that despite using 3 access points, I still don’t have a fully functional Inseton network?AnonymousJuly 7, 2008 at 3:46 pmPost count: 1001
I have linked ICON and Smarthome Lamplincs and Keypadlincs to my EZSrve. What Smarthome devices have you not been able to use? When you added those devices to EZSrve, was the link established successfully?
Access Points serve two purposes. They provide the RF send/receive capability for wireless devices such as the Remotelinc and the Thermostat Adaptor. The more Access Points you have, the larger the RF coverage area. The second function of Access Points is to provide cross phase communication. Insteon messages on one power line phase are repeated on the other power line phase via the RF capability of the Access Point. For this to work there has to be an Access Point plugged into a receptacle on both power line phases. If the three Access Points are powered from the same power line phase, it is as though you had no Access Points as far as phase coupling is concerned.AnonymousJuly 10, 2008 at 5:17 amPost count: 4
My problem is not with the linking of the units. What was happening is I was getting an error message when trying to add responders to the scene. I was getting the following message when trying to save the scene:
No Response From Device 0A.F4.B4 ! Please Ensure Device is Active.
On occasion, EZServe would also keep me from adding a responder before saving the scene. In every case the unit in question would respond to EZServe On, Off, and Dim commands without a problem.
I am now getting the scenes saved and devices added. However, I will sometimes get the above message anyway.
As I indicated above, I have three access points. Two are on separate phases the third is near some computers I have in order to get a bathroom unit to function properly.
I added three new in-wall Icon dimmers this weekend and the communication seems to be getting better as the scene error message is occasional as opposed to every time.
Do I need more access points or just more Insteon units around the house to help boost the signal?[/b]AnonymousJuly 10, 2008 at 8:46 amPost count: 1001
The more Insteon devices you add, the better things tend to get because each Insteon device repeats messages. I’m thinking the benefit you gained by adding an Access Point near the computers was the result of that repeating, not from RF coupling (assuming that 3rd access point did not establish the coupling). Plugging in a LampLinc or ApplianceLinc might have provided the same gain. I would think about installing a FilterLinc between the computer(s) and the power line. Computer power supplies (and some TVs and UPSs as well) want to keep noise to minimum and act as signal suckers. Don’t like that term but it seems to be what folks use to describe the condition. I’ve installed a FilterLinc on each of my computers/UPS installed in different locations in the house and it has helped. You can unplug the TVs, computers and UPSs you don’t need to test Insteon (not just turn them off) and see if that helps. If so, then they need a FilterLinc. As an FYI, when you save a Scene you are linking devices.AnonymousJuly 12, 2008 at 6:13 pmPost count: 4
Thanks! Things are getting better. I’ll look into the FilterLinc.
- You must be logged in to reply to this topic.