AnonymousApril 21, 2008 at 3:55 amPost count: 4
Using a brand new EZServe with 1.42. I can set up timers just fine. I can test devices manually in view/manage areas. But, the timers don’t do anything. I’m at a loss – what am I doing wrong? 😥AnonymousApril 21, 2008 at 3:25 pmPost count: 408
Sorry about your problems. A couple of questions
1) Did you setup your timezone?
Go to the setup area, and select your timezone. If it is showing the timezone as correct, change the timezone, apply it, and then change it back to the correct value. This is a bug that happens rarely – will be fixed in 1.50.
2) Did you setup your location?
Go to the setup area, you can locate your latitude / longitude and then apply it. This is only required for sunrise / sunset.
3) Have the timers ever worked and just work occasionally, or do they never work.AnonymousApril 21, 2008 at 3:31 pmPost count: 4
Yes I have set up my timezone and location numerous times, restarting and resetting numerous times. No joy. The time is right, the timezone is right, even the sunrise/sunset times look good.
The timers have never worked, so I suspect I did something wrong in the setup. Thanks.
MauriceAnonymousApril 21, 2008 at 3:32 pmPost count: 408
Can you email me your timer.xml file – it can be found under backup / restore. Select backup, go tot he file, right click to save as, and then email
paul at simplehomenet.com
I will take a look at it and get back to you.AnonymousApril 22, 2008 at 2:39 amPost count: 69
Maurice, are your timers controlling insteon devices or x10? I’ve had no problems with the timers controlling insteon, but I’ve never been able to get them to work with x10.AnonymousApril 22, 2008 at 2:50 amPost count: 408
We have found a bug, it appears to be related to X10 timing – we are going to have this fixed in 1.50.
I am sorry for the trouble!AnonymousApril 22, 2008 at 3:05 amPost count: 4
OK, no problem, thanks for chaseing it down. If you want a beta site let me know – I also own an X10 analyzer.
MauriceAnonymousApril 24, 2008 at 3:25 amPost count: 4
Any word on when the 1.5 firmware will be available?AnonymousApril 24, 2008 at 7:32 pmPost count: 408
See the thread belowAnonymousApril 25, 2008 at 3:05 amPost count: 4
Great News on 1.50!!!
Let me know if you want me to test it.. since right now nothing works at my house… 🙁AnonymousApril 28, 2008 at 10:35 pmPost count: 408AnonymousApril 30, 2008 at 4:42 amPost count: 69
My timers fired tonight after 1.43 and no PLM errors so far. Good job, guys!
- You must be logged in to reply to this topic.