Intro: I have just gotten the first KPL, and I have linked it with a test load (lamp) just fine. I also have the RemoteLinc controlling the load, so I established a cross-link between the KPL and the RL. So far everything is good. I can turn the load on or off from either device (KPL/RL), and the LED on the KPL is reflecting the correct status of the load.
Problem: I also have an action defined in EZServe that will turn on/off the load/lamp; however, I cannot get this action to correctly reflect the load status on the KPL.
I have tried to link the KPL as a responder to the EZServe using both the set buttons and the Utility Suite, but I am not getting anywhere.