Oddly EZFlora stopped responding to EZServe after 3 days. I have two EZFlora units and both behave the same way. I can link to them, read timer values, write timer values but I cannot get the units to turn on values either manually control or via programs.
This was on version 2.01
Reset via web interface – no change
Upgraded to 2.03 – no change
HARD reset – no change
Linked directly to PLM via set button on EZS – no change
Downgrade to 1.6 – Works perfectly.
Any ideas. I only have EZFlora installed, one area, no actions ie minimal config.
Solved – shorted valve – I guess the manual operation of the sprinkler valve (while waiting for the EZFlora) and the associated water on the solenoid from the bleeder valve caused the solenoid to short out – the solenoid is older and not plastic like the current generation.
The shorted valve #2 would cause the PTC in the xfrmr (or EZFlora?) to trip making it appear that the EZFlora wasn’t advancing the program.
The whole EZServe s/w version was simply the PTC reseting and making it appear like the S/W made a difference.
Arrrgh – I wasted 5 hours TFTPing, reseting EZFlora / EZServe all for a broken sprinkler valve 🙁