AnonymousInactiveJanuary 11, 2008 at 3:07 amPost count: 11
I recently bought an EZBridge so I could use the SimpleHomeNet utility to program my EZX10RF and EZIO2X4. Messed around with it most of a weekend. The SimpleHomeNet utility mangles device link tables, and is unable to write the values to the EZX10RF virtual inputs. I also was unable to write the EZIO2X4 Insteon AllLink Group commands. The whole reason that I bought the EZBridge was to SIMPLIFY the programming of the EZX10RF and EZIO2X4 by using the SimpleHomeNet utility. Now it seems that it is simpler to run around the house pressing the little buttons in a magic sequence.
I have tried this utility on a Win2000, WinXP and Vista machine. Same results on all.
Have any of you had good luck with the SimpleHomeNet utility? If so, which modules has it helped you program? Do you use the utility with a PLC or an EZBridge?AnonymousInactiveJanuary 11, 2008 at 5:16 pmPost count: 256
The utility is not really a general purpose device database manager that lets you write to all classes of device link databases. One big limitation is that there are 2 types of databases. All our devices and those based on the PLM have the so-called linear database and the utility handles those fine. All legacy devices, however, have a linked-list type database that our utility does not yet recognize.
Additionally, there is currently a bug in the PLM from Smartlabs where its firmware does not respect the MSB when writing (poking) into the Insteon device memory space. This affects devices that are built on a PLM that does not have external memory (EZIO2X4, EZIO5I, EZIO4O, EZX10RF and EZRain.) This results in the observed “mangling” of the database when writing to the other parameters (input parameters, timers, config. register, etc.)
To get around this, do the linking, note the written links, modify the input parameters as desired, and then re-write the links.
The utility woerks faster and more reliably with the EZBridge than with the PLC.
A browser interface will be available shortly that eases adding devices to the system. All current owners of EZBridge will be entitled to a free upgrade. Our strategy will be to concentrate on facilitiating device management as we recognize this is the missing (NPI) link.AnonymousInactiveMay 14, 2008 at 8:42 pmPost count: 26
Just curious if the PLM bug is one they ever fixed, and if so, what PLM revision. Thanks
- You must be logged in to reply to this topic.