Turns out this problem is related to the class of device rather than Access Points alone. A “Controller Only” device cannot be the first device definition following EZServe in the devices3.xml file. A ControLinc, an Access Point, a Remotelinc, any device type that has no responder function cannot be the first device following EZServe. The symptom remains the same, the Timer and Macro device pulldown displays blank lines. Should you have this symptom carefully edit the devices3.xml file, moving something other than a Controller Only type device into Device Rec=”1″ position. The Device Rec=”x” values will have to be adjusted in each of the Device Rec=”x” tags to put them back into ascending sequence.
Reply To: EZServe Timer can’t see devices 2017-12-26T17:13:25+00:00