HOME › Forums › Input/Output › EZIOxx › EZServer 1.58 error message "link could not be created& › Reply To: EZServer 1.58 error message "link could not be created&
Not all Smarthome and Simplehomenet products support adding that link when the device definition is added to EZSrve. That is one of the reasons the option “Would You Like To Create An Insteon Link? is provided when the device definition is Saved. Select NO when asked that question. It is not required for the EZIO2X4 to function correctly. All the linking and macro activity that I posted earlier was done with one of my V25 EZIO2X4s that was added with the NO option. You will have the same situation if you add a Smarthome ControLinc to EZSrve. Select NO when adding a ControLinc. Just as with the EZIO2X4, it has no affect on the operation of the ControLinc.
EDIT: For the ToggleLinc to activate an Output relay, use EZSrve Scenes Management to create a link between the ToggleLinc and the EZIO2X4. The ToggleLinc will be the controller, Unit 01. The EZIO2X4 will be the responder with LD1 00, LD2 00, LD3 00 to control Output Relay 1. Set LD3 to 01 to control Output Relay 2. There are other combinations of data that LD1,LD2,LD3 can be set to for the ToggleLinc to set the Output Relays to a predefined pattern of On and Off. Refer to the EZIOxx Link Records document in the Downloads section for a description of the various combinations that can be specified in LD1,LD2,LD3.