I can confirm with a direct test that an EZIO2X4 device can be added to EZSrve (select NO when asked if a link should be created) when the device Save is done. Once the EZIO2X4 device is defined it can be used in the “Then Device:” clause of a macro. The “Does:” field has an Output2-ON and Output2-OFF option which provides for Output Relay 2 to be turned ON or OFF with a macro. The macro can be triggered with an ON or OFF from an EZSnsRF. When an ON is received from the EZSnsRF a macro is triggered that turns ON the EZIO2X4 Relay 2. When an OFF is received from the EZSnsRF a macro is triggered that turns OFF the EZIO2X4 Relay 2 with a time delay. I confirmed with a meter that Relay 2 was turned ON and OFF with those two macros.
Reply To: SHM Clarification2017-12-21T14:50:52-08:00