For another week I have been unsuccessful in recreating a timer failure. Now have 22 Sunset+ timers controlling 1 Insteon Lamplinc and 3 X10 flood lights. The X10 devices were initially unreliable but this was caused by problems with my power line. The timer commands were always issued and traced by Houselinc Desktop and an X10 Signal Analyzer, even when the X10 devices themselves did not always respond. My EZSrve was originally plugged into a surge protected power strip and I added a Filterlinc between the UPS and the power line. After moving EZSrve to the correct power strip and installing the Filterlinc, I have reliable X10 device response.
Twenty two timers firing at Sunset+ n minutes
+0 Lamplinc ON F2 ON
+1 F3 ON
+2 F4 ON F2 OFF
+3 F3 OFF F4 OFF
+4 F2 ON F3 ON F4 ON
+5 F3 OFF
+6 F4 OFF
+7 F2 OFF
+15 Lamplinc OFF
+35 Lamplinc ON F3 ON F4 ON F2 ON
+36 Lamplinc OFF F3 OFF F4 OFF F2 OFF
Power Line activity monitored/traced by Houselinc Desktop software and a Power Line Signal Analyzer by Monterey Instruments.
With 1.51 just around the corner, I expect this will be my last full week Timer test on 1.50.